How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
What is code requirement for receptacle outlets at a porch, deck, or balcony?
Monday, April 11, 2022
At least one receptacle outlet is required for any porch, deck, or balcony that is within 4-inches horizontally of a house, according to the 2020 edition of the National Electrical Code [NEC 210.52(E)(3)]. Here’s how it’s stated: "Balconies, decks, and porches that are within 102mm (4 in.) horizontally of a dwelling unit shall have at least one receptacle outlet accessible from the balcony, deck, or porch. The receptacle outlet shall not be located more than 2.0 m (6-1/2 ft) above the balcony, deck, or porch walking surface." Also, like any other exterior receptacle outlet, it must be GFCI-protected.
The wording of this requirement has been tweaked over the last several editions of the the code. Earlier editions had specified that the requirement was only for a balcony, deck, or porch that was directly attached to and accessible from the inside of the residence. Also, the required receptacle outlet had to be located within the perimeter of the balcony, deck, or porch. Now the receptacle outlet only has to be accessible from it.
• • • • • • • • • • • • • • • • • • • • • • • • • •
To learn more about electrical receptacles outlets, see these other blog posts:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.