How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
Can you substitute two 120-volt breakers for a 240-volt breaker in a panel?
Friday, April 15, 2022
Yes, you can use two side-by-side single-pole 120-volt breakers as a substitute for a two-pole 240-volt breaker as long as the following three requirements are met:
1) The breakers must be “specified" as suitable for installation in the panel by the same company that manufactured the panel box, or “classified” by a recognized rating agency like UL as an acceptable alternative by a different manufacturer. See our article What is the difference between specified and classified circuit breakers? for more on this.
2) The breakers should be marked as rated for both 120 and 240-volt usage by the manufacturer.
3) You must connect the two breakers with a handle tie rated for use with that company’s breakers. An improvised connector, such as a piece of wire, is not acceptable and may allow one breaker to trip without the other.
• • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our other blog posts about CIRCUIT BREAKERS:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
Buying a home in North/Central Florida? for a team inspection by two FL-licensed contractors and inspectors. Over 8,500 inspections completed in 20+ years. In a hurry? We will get it done for you.