How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
Can an electrical panel be located at a stair landing?
Thursday, October 14, 2021
It’s acceptable as long as the landing meets the code requirement for a safe access area in front of the panel: 2’-6” wide by 3’-0” deep level floor below it, and 6’-6” high clear above floor in front of it [NEC 110.26 (A)(1,2,3)]. The panel is not required to be centered in the 2’-6” width, but the panel door must be capable of swinging open to 90º (perpendicular).
Just because you can do it does not mean it’s a good idea. We have inspected condo units with the panel at the top landing of a stair and compliant with the service access requirement, but positioned so that, if you stepped backwards from the panel beyond the 3’-0” depth, you fell down the stairs.
For more on this requirement and its history, go to When did the requirement for clearance in front of an electrical panel become code? Also, see our articles Can an electrical panel be located under stairs? and Can an electric panel be located over stairs?
• • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of some of our other blog posts about ELECTRIC PANELS:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
Buying a home in North/Central Florida? for a team inspection by two FL-licensed contractors and inspectors. Over 8,500 inspections completed in 20+ years. In a hurry? We will get it done for you.