How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manufactured and modular homes
How many NM-cables allowed in an NM-connector clamp?
Saturday, August 8, 2020
The National Electrical Code does not adress the issue of how many cables are allowed in a single connector. It only states that “where cable is used, each cable shall be secured to the cabinet…” [NEC 312.5(C)]. The number allowed is based on the UL-rating. Most NM-connectors are UL-approved for securing only one NM-cable to a panel box. But some are rated for two #14 or #12 cables, and we know of one 3/4” connector that is rated for three.
Check the box for the number approved by the manufacturer, but it’s definitely not more than three. So the example shown at the arrow above, that clamps a total of five NM-cables (one is hidden in back) is not acceptable.
• • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our other blog posts about ELECTRIC PANELS:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
Buying a home in North/Central Florida? for a team inspection by two FL-licensed contractors and inspectors. Over 8,500 inspections completed in 20+ years. In a hurry? We will get it done for you.