How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
Does a wall or window room air conditioner need a dedicated circuit?
Thursday, May 14, 2020
All 120-volt wall or window air conditioners that are around 8,000 BTU or more will have a sticker on the side, like the one shown above, that require a “single outlet” (dedicated) circuit. The reason is that the National Electrical Code (NEC) requires that any cord-and-plug connected appliance that is fastened in place be limited to 50% of the rating of a multiple outlet circuit to which it is connected. NEC 210.23(A)(2) states that: “The total rating of utilization equipment fastened in place, other than luminaries, shall not exceed 50-percent of the branch-circuit ampere rating where lighting units, cord-and-plug-connected utilization equipment not fastend in place, or both, are also supplied."
So a wall/window air conditioner with a rating of over 7.5 amps would require its own circuit on a 15-amp breaker, or over 10-amps on a 20-amp breaker. If the applliance is not “fastened in place,” such as a portable dehumidifier, then it is allowed to be up to 80% of circuit rating, per NEC 210.23(A)(1).
• • • • • • • • • • • • • • • • • • • • • • • • • • • •
To learn more about heating and air conditioning systems, see these other blog posts:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
Buying a home in North/Central Florida? for a team inspection by two FL-licensed contractors and inspectors. Over 8,500 inspections completed in 20+ years. In a hurry? We will get it done for you.