How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
Where should smoke alarms NOT be installed?
Friday, April 3, 2020
The logic behind where smoke alarms should NOT be installed is simply to avoid locations where they will not function properly or the environment may damage the unit. Here’s our list, with an explanation for each one:
• In a kitchen, or near a kitchen in a location where air currents will draw cooking smoke into alarm sensor and cause frequent false alarms.
• Near fluorescent lights. The electrical field around the transformer in the light may interfere with alarm function. Keep a minimum of one foot away.
• In a bathroom, or any other humid, steamy area. This will deteriorate the sensors over time and may cause false alarms. Keep smoke alarms at least 10 feet away from dishwashers, showers, saunas.
• In any non-living-areas with temperature extremes, below 40º F or above 100º F, such as a garage, outdoor rooms, unfinished attics, or basements.
• Anywhere near where combustion particles are produced by something burning. Keep as far away as possible from any gas furnace, water heater, range, or space heater.
• Near a/c ducts and ceiling fans, and any drafty areas. The air flow may divert any smoke away from the alarm sensor.
• In any corners at ceiling and wall intersections, or above cove moldings or shelving, which would create “dead air” pockets that smoke will flow around. See the diagram and photo below.
Also, see our blog posts Where are smoke alarms required to be located? and Does pushing the test button on a smoke alarm test the smoke sensor device inside? and When should I replace my smoke alarms? and Is it illegal to disconnect a smoke alarm? and Are carbon monoxide alarms required to be installed in homes in Florida?
• • • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our blog posts about SAFETY:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
Buying a home in North/Central Florida? for a team inspection by two FL-licensed contractors and inspectors. Over 8,500 inspections completed in 20+ years. In a hurry? We will get it done for you.