Does every receptacle outlet in a kitchen have to be GFCI?
Saturday, February 1, 2020
Only receptacle outlets that are "installed to serve the countertop surfaces” in a kitchen must be GFCI-protected in a residence, per National Electrical Code [NEC 210.8(A)(6)]. For buildings other than dwellings, all receptacles in a kitchen must be GFCI-protected [NEC 210.8(B)(2)].
So wall receptacles in a residential kitchen are not required to be GFCI, but there is one exception: any receptacle that is within 6-feet of a sink, even if not serving a counter, must have GFCI-protection. A common example of this would be a refrigerator receptacle outlet close to a kitchen sink. This was not always required and, to read more about it, go to our blog post Is a refrigerator receptacle outlet required to be GFCI-protected?
• • • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our other blog posts about AFCI and GFCI RECEPTACLES AND CIRCUIT BREAKERS:
How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.