Does a subpanel require a main breaker by code?
Sunday, February 2, 2020
The means of disconnection for a subpanel is provided by a breaker serving it in the service (main) panel, so an additional breaker at the subpanel is not necessary. But you can put a main breaker at a subpanel is you want. The National Electrical Code only requires a main disconnect for a subpanel when located in a separate building (NEC 225.30 and 225.31).
The means of disconnection can use up to six switch-throws [NEC 225.33(A)]; so, even if the subpanel is in a separate building, if the panel has a total of six breakers or less you’re good. Also, main disconnect(s) must be marked as such.
• • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our other blog posts about ELECTRIC PANELS:
How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.