How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
Does a combination microwave and range hood need a separate dedicated circuit?
Sunday, December 6, 2020
A combination microwave/hood cannot be connected to the either of the two required kitchen small appliance receptacle circuits because it is not a countertop (portable) appliance, per National Electrical Code [NEC 210.52(B)(2)]. It’s a fixed appliance. Also, all the manufacturer’s manuals for microwave/hoods that we have seen specify a dedicated circuit, preferably 20-amp, and the NEC requires following manufacturer’s installation instructions for listed and labeled appliances [NEC 110.3(B)].
To find out more about microwaves and range hoods, see our blog posts Does a home inspector check for dedicated circuits? and Is a range hood exhaust fan required in the kitchen? and Do microwaves require any minimum clearances around them? and What are the most common defects with over-the-range microwaves? and What is the maximum recommended height above the floor for an above-the-range microwave?
• • • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of some of our other blog posts about APPLIANCES:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
Buying a home in North/Central Florida? for a team inspection by two FL-licensed contractors and inspectors. Over 8,500 inspections completed in 20+ years. In a hurry? We will get it done for you.