How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manufactured and modular homes
Is a sink or toilet shut-off valve behind an access panel approved by code?
Thursday, October 15, 2020
The International Plumbing Code (IPC) allows a fixture shut-off valve to be in an accessible location. Accessible is defined as “access that requires the removal of an access panel or similar removable obstruction.” So the shut-off valve behind a removable panel in the wall next to the toilet is acceptable.
But the installation shown above has another problem. According to IPC 604.5 “the supply pipe shall extend to the wall behind the fixture.” So, although the shut-off is okay, the pipe has to protrude from the wall before the compression fitting and flexible hose can be connected—which it doesn’t.
Irregardless of code, this installation does not meet normal plumbing trade standards. A leaking shut-off valve or compression fitting in the wall would not be noticed until water began puddling in the adjacent rooms.
• • • • • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our blog posts about SHUT-OFF VALVES:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
Buying a home in North/Central Florida? for a team inspection by two FL-licensed contractors and inspectors. Over 8,500 inspections completed in 20+ years. In a hurry? We will get it done for you.