What is an electrical "dead front"?
Friday, January 10, 2020
The National Electrical Code (NEC) defines dead front as “without live parts exposed to a person on the operating side of the equipment.” So it means the component is not electrically live and does not have the potential to become live. This metal plate with openings to expose the breakers in the front of an electrical panel is one type of dead front. It protects anyone touching it from shock in two ways: the metal is isolated from the live parts of the panel and also grounded—so that, if the dead front does somehow briefly become live, the current flow to ground will immediately trip a breaker to shut off the electricity. A dead front can also be a non-conductive material, such as plastic at a dead-front type GFCI device or the face of a dead front plug.
• • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our other blog posts about ELECTRIC PANELS:
How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
for Links to Collections
of Blog Posts