How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manufactured and modular homes
How far away does a dryer have to be from an electrical panel?
Wednesday, January 29, 2020
Nothing is allowed to be installed in a working space 2’-6” wide by 3’-0” deep by 6’-6” high in front of an electric panel, per National Electrical Code [NEC 110.26 (A)(1)]. That includes a washer, clothes dryer, water heater, pool equipment, water treatment equipment, shelving or a counter.
The panel does not have to centered in the 2’-6” width, although it is shown that way in the diagram above, and the panel box can protrude up to 6” into the space.
While this might seem like overkill since a dryer can be disconnected and moved out of the way with a few minutes work so that an electrician or home inspector inspector have the necessary safe working space, getting immediate access to a panel may be necessary in an emergency. Climbing or leaning over equipment that is likely to be grounded to get at the panel is dangerous and, equally important, a quick escape route in case of arcing when in front of the panel is also necessary.
• • • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of some of our other blog posts about APPLIANCES:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
Buying a home in North/Central Florida? for a team inspection by two FL-licensed contractors and inspectors. Over 8,500 inspections completed in 20+ years. In a hurry? We will get it done for you.