How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manufactured and modular homes
Why do the manufacturers of many 120-volt wall/window air conditioners specify USE ON SINGLE OUTLET CIRCUIT ONLY.
Friday, August 9, 2019
Most general purpose wall receptacle outlets that you would plug a window air conditioner into are rated at 15 amps. The National Electrical Code (NEC) requires that any cord-and-plug connected appliance that is fastened in place be limited to 50% of the rating of a multiple outlet circuit to which it is connected. So a wall/window air conditioner with a rating of over 7.5 amps would require its own circuit. If the applliance is not “fastened in place,” such as a portable dehumidifier, then it is allowed to be up to 80% of circuit rating.
Also, see our blog post What are the most common problems with wall/window air conditioners?
Here’s links to a collection of our blog posts about APPLIANCES:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
Buying a home in North/Central Florida? for a team inspection by two FL-licensed contractors and inspectors. Over 8,500 inspections completed in 20+ years. In a hurry? We will get it done for you.