How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manufactured and modular homes
Why is the mini-split ductless air conditioner installed in a sunroom enclosed with acrylic plastic windows called a “dehumidifier” on the building permit?
Monday, July 1, 2019
It is likely that the sunroom was originally a screen porch that has been enclosed. Unfortunately, simply enclosing the room with clear acrylic plastic windows does not make it acceptable by the building code for air conditioning and to be considered as “habitable space.”
The code requires that conditioned (heated and cooled) spaces be insulated, and clear plastic panels have minimal insulation value. There is also usually no insulation above the ceiling. The builder did not install it there because insulation is not necessary over a screen porch, and it is often difficult to retrofit. To complicate things further, the floor of the former screen porch should be at the same level as the main living area, which it is often not.
Then some ingenious person noticed that many mini-split heat pumps also have a “dry” mode, besides cooling and heating, so they can be used as dehumidifiers that only activate when necessary to lower the humidity in the room. And they were able to convince the building department that it was alright to issue a permit for the installation of a mini-split in a sun room as long as it was intended only for dehumidifcation. Yeah, sure…that’s a very expensive dehumidifier. Also very popular here in The Villages and surrounding retirement communities.
While this not exactly a defect, we try to point out these two things to homebuyers:
- Because the HVAC unit is supposedly only a dehumifier, the sunroom (sometimes referred to as an enclosed lanai) is not considered a heated and cooled, habitable conditioned living space. And if the square footage of the sun room is showing up on the real estate listing for the house as part of the living area square footage that you pay premium dollars for, it probably shouldn’t be.
- The room will be also expensive to heat and cool because of lack of adequate insulation.
The Residential Edition of the Florida Building Code (R301.2.1.1.1) has five categories for sunrooms:
- Category I is an open or screened porch.
- Category II is “a thermally isolated sunroom with enclosed walls. The openings are enclosed withtranslucent or transparent plastic or glass. The space is nonhabitable and unconditioned.”
- Category III is “a thermally isolated sunroom with enclosed walls. The openings are enclosed with translucent or transparent plastic or glass. The sunroom fenestration complies with additional requirements for air infiltration resistance and water penetration resistance. The space is nonhabitable and unconditioned."
Sunrooms with a mini-split “dehumidifier" are in Category II or III. In order to qualify to be a conditioned—but still not habitable—space, the room must comply with Category IV, which means weather-resistant and insulated. Only Category V can be habitable and conditioned, and it has to be weather-resistant, insulated, and open to the main living area. As a habitable space, Category V must also be compliant with electric receptacle outlet spacing and lighting requirements.
• • • • • • • • • • • • • • • • • • • • • • • • • • • • • • • • •
To learn more about heating and air conditioning systems, see these other blog posts:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
Buying a home in North/Central Florida? for a team inspection by two FL-licensed contractors and inspectors. Over 8,500 inspections completed in 20+ years. In a hurry? We will get it done for you.