When did the requirement for clearance in front of an electrical panel become code?
Tuesday, December 31, 2019
The current standard for clearance in front of an electrical panel for working space began with the 1978 edition of the National Electrical Code (NEC). NEC 110.26 (A)(1) requires a clear area for access and working in front of an electric panel that is 2.5 feet (30”) wide, 3 feet (36”) deep, and 6.5 feet (78”) high for a regular residential 120/240-volt panel. The 2.5 foot width in front of the panel does not have to be centered, although it is shown that way in the diagram.
Previous to 1978, the depth requirement was 2.5 feet, and up until 1965 it was 2 feet. The 2.5 feet width requirement began with the 1971 edition of the code. The panels shown below and at the top of the page are not acceptable, no matter how old.
• • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our other blog posts about ELECTRIC PANELS:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes