Why is there a lock on the circuit breaker?
Saturday, August 4, 2018
The National Electric Code (NEC 422.30) requires that an installed electric appliance be able to be shut off by the a person servicing it and that the shut-off device either be within sight of the appliance, or lockable if not within sight—in other words, under their control. The intention of this requirement is to avoid the possibility of someone turning the electricity back on while the technician is handling the appliance wiring and liable to be shocked.
A lock device on the front of a breaker in an electric panel is usually for a water heater at a location that is not within sight of the panel, but it could be used for any other major appliance except an air conditioning condenser (outside unit), which the National Electric Code (NEC 440.14) requires that the shut-off device must always be within sight.
Another type of breaker locking device you might see is shown below.
Here’s a list of four other acceptable shut-off devices besides a circuit breaker lock:
1) Cord plugged into a receptacle outlet within sight - The simplest of all solutions: pull the plug and you’re good.
2) A wall switch within sight - This is handy for people that like to turn off their water heater when not home, and a switch that lights up when on is often used. A wall switch is also sometimes installed for furnaces and air conditioning air handlers, located on the wall near the unit. The only
problem with this means of shut-off is that occasionally a family member mistakes it for a light switch, turns it off, and then later the air conditioner mysteriously has stopped working.
3) A circuit breaker at panel within sight - Must be within sight of both the appliance and panel.
4) Pull-disconnect box within sight - This is the most common disconnect method for new homes. The circuit breaker switch may not have an amperage rating number on it, because it does not have to provide overcurrent protection if it is already provided by a breaker at the main panel.
• • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our other blog posts about ELECTRIC PANELS:
How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.