How To Look At A House

site-built, mobile/manufactured and modular homes

What is the voltage rating of a house electrical system?

Wednesday, July 11, 2018

Although people commonly refer to the voltages as “110” and “220” for household current, that was actually just the original voltage for early alternating current systems. The two “hot” (ungrounded) wires serving the first  systems were 110-volts each and, when both were used for a major appliance, the total voltage was 220. Voltage was set at these numbers early in the 20th century so the newer alternating current (AC) systems, designed by Nikola Tesla and manufactured by George Westinghouse, could be compatible with the existing wiring of the older direct current (DC) systems installed in many communities by Thomas Edison. Edison’s DC system suffered from rapid voltage drop over even short distances, and was eventually completely abandoned.

The voltage provided by local utility systems was ramped up to 115/230 by the 1930s, and then edged up again to 120/240 by the 1980s. The American National Standards Institute (ANSI) now requires that electric utility voltages not deviate more than 5%, and the voltage delivered to the home can be adjusted at the transformer to accommodate voltage loss by a longer distance from transformer to house.

So, the voltage delivered to homes with single-phase service today is 120/240, and some are rated at 125/250, except for an occasional large house or apartment building with 3-phase service (3 hot wires). This type of system provides 120 volts to the neutral or ground, and 208 volts between the hot conductors.

But when our customers refer to the “220 breaker for the dryer” or the “110 wall plug,” we don’t correct them. Everybody understands exactly what they are talking about.

• • • • • • • • • • • • • • • • • • • • • • • • • • •

Here’s links to a collection of our other blog posts about ELECTRICAL WIRING:

Which house appliances need a dedicated electrical circuit?

Can a short circuit cause a high electric bill?

What is the maximum spacing requirement for securing NM-cable (nonmetallic-sheathed cable)?

Is it alright to just put wire nuts on the end of unused or abandoned NM-cable or wiring?

What causes copper wires to turn green or black in an electric panel?

What are typical aluminum service entrance wire/cable sizes for the electrical service to a house?

Why is it unsafe to bond neutral and ground wiring at subpanels?

Should I get a lightning rod system to protect my house?

Why is a strain relief clamp necessary for the cord connection to some electric appliances?

Does a wire nut connection need to be wrapped with electrical tape?

What is the minimum clearance of overhead electric service drop wires above a house roof?

What are the requirements for NM-cables entering an electric panel box?

Visit our ELECTRICAL page for other related blog posts on this subject, or go to the INDEX for a complete listing of all our articles.

Water Heaters

Water Heater Age

"What Are The

Signs Of..."

Septic Tank Systems

Structure and Rooms

Plumbing Pipes

Termites, Wood Rot

& Pests

Sinkholes

Stairs

When It First

Became Code

Park Model Homes

Site

Shingle Roofs

Safety

Stucco

Remodeling

Wind Mitigation

Roof and Attic

"Does A Home

Inspector...?"

Pool and Spa

"What Is The Difference Between..."

Brick

Plumbing

Concrete and

Concrete Block

Metal Roofs

Foundations

Modular Homes

Rain Gutters

Condominiums

Older and

Historic Houses

Crawl Spaces

Mobile-Manufactured Homes

Building Permits

Life Expectancy

Clay Soil

Insurance

Floors

Insulation

Toilets

Exterior Walls

& Structures

Generators

Common Problems

HUD-Code for

Mobile Homes

Garages and Carports

Flat (Low Slope) Roofs

Electrical Panels

Sprinkler Systems

Electrical Receptacle Outlets

4-Point Inspections

Hurricane Resistance

Home Inspection

Heating and Air Conditioning

Building Codes

Fireplaces and Chimneys

Inspector Licensing

& Standards

Energy Efficiency

Washers and Dryers

Electrical

Kitchens

Doors and Windows

Cracks

Electrical Wiring

Click Below

to Collections

of Blog Posts

by Subject

Plumbing Drains

and Traps

Appliances

Smoke & CO Alarms

Aging in Place

Top 5 results given instantly.

Click on magnifying glass

for all search results.

Bathrooms

Lighting

AFCI, CAFCI,

DFCI, & GFCI

Sinks

Air Conditioner & Furnace Age/Size

Attics

Electrical Switches

Siding

Search

This

Site

Water Intrusion

Electrical - Old

and Obsolete

Foundation Certifications

Tiny Houses