How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
How many electrical receptacles (outlets) are required in a hallway?
Thursday, July 12, 2018
The International Residential Code (IRC E3901.10) only requires an electric receptacle in a hallway that is 10 feet or longer, and only one is required. Longer halls do not require any additional receptacles. That does not mean that you can’t put a receptacle in a hallway shorter than 10 feet, or put multiple receptacles in a very long hallway. It’s just not required. The spacing requirement for many other rooms in a home (not more than 6 feet from any point along the base of a wall to a receptacle) does not apply to hallways. Also, see our article What is the minimum width of a hallway?
There are different standards for bathrooms, closets, hallways, foyers, kitchen, stairs and stair landings, garage, or outdoor receptacles. See our blog posts How far apart should the electrical receptacles be placed? and How far apart should electric receptacles be spaced in a bathroom? and What is the code requirement for receptacle outlets in a closet? and How many electrical receptacle outlets are required in a hallway? and How far apart should kitchen counter receptacles be spaced? and How far apart should electric receptacle outlets be placed in a garage? and What is the building code requirement for receptacle outlets at stairs and stair landings? and What is the code requirement for receptacle outlets in a foyer? and Is a house required to have outdoor electric receptacle outlets?
• • • • • • • • • • • • • • • • • • • • • • • • • • • • • • • • • • • •
To learn more about electrical wiring, devices, and receptacles, see these other blog posts:
• What is the difference between what trips a GFCI (ground fault) receptacle and a circuit breaker?
• What is the code requirement for GFCI protection for receptacles near a wet bar sink?
• What is the requirement for a service receptacle outlet for heating, air conditioning, and refrigeration (HACR) equipment?
• Why is an opening in the wall around the side of an electrical receptacle outlet a safety defect?
• When was GFCI-protection for kitchen dishwasher receptacle outlet first required?
• What is allowable voltage range at a wall receptacle outlet in a house?
• When should I replace electric receptacle outlets?
• Does an electric receptacle outlet in a storage shed require GFCI protection?
• What are "self-contained" electrical receptacle outlets and switches?
• What is the difference between an electrical receptacle, an outlet, and a plug?
• Does a washing machine receptacle outlet require GFCI protection?
• Can I remove a 240-volt range receptacle and hard-wire the range?
• What is a "backstab" receptacle outlet?
• Why are some electric receptacle outlets upside down (ground slot up) in a house?
• What is the height requirement for an electric receptacle outlet?
• Where are GFCI receptacle outlets required?
• When were GFCI receptacle outlets first required?
• Does a home inspector remove receptacle outlet cover plates?
• What is the minimum height for an exterior receptacle outlet?
• When was the current receptacle/outlet spacing of 12-feet first required?
• When was the three-slot (grounding) outlet/receptacle first required?
• Why does painting an electric receptacle (outlet) make it unsafe?
• Why are electrical outlets and plugs polarized?
• What problems does having too many electric receptacle outlets on a single circuit cause?
• How I can tell if a receptacle outlet is tamper resistant?
• Why is there a GFCI breaker in the electric panel for the bathroom shower light and exhaust fan?
• What is a false ground, bootleg ground, or cheated ground receptacle?
• How can adding wood paneling or a wainscot create an electrical safety hazard?
• How far above a kitchen countertop do electrical outlets have to be?
• What is reversed polarity at an outlet/receptacle? Why is it dangerous?
• How high above the floor do electric outlets/receptacles in a garage have to be?
• Is an ungrounded electric receptacle outlet dangerous?
• My bathroom electric receptacle/outlet is dead and there are no tripped breakers in the electric panel. What's wrong?
• Is there an adapter that can be placed on a two-slot receptacle to make it safe?
• How do the new tamper-resistant electric outlets work?
• Why is there no bathroom electric receptacle in this old house?
• How can I tell if the electric receptacle outlets are grounded?
• What are the most common problems/defects found with electric receptacle outlets during a home inspection?
Visit our ELECTRICAL page for other related blog posts on this subject, or go to the INDEX for a complete listing of all our articles.
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
Buying a home in North/Central Florida? Check our price for a team inspection by two FL-licensed contractors and inspectors. Over 8,500 inspections completed in 20+ years. In a hurry? We will get it done for you.