Does an electric water heater require a disconnect?
Wednesday, July 11, 2018
When someone is repairing an electric water heater, they need to be assured that the electricity stays off while they are handling wiring and connections that could shock or kill if the circuit were to suddenly become “live.” So the building code addresses this safety issue by providing several choices of solutions that make the means of disconnecting the circuit either within sight or under the exclusive control of the person working on the water heater.
Here are the five options:
1) Panel within sight - If the main electric panel or a subpanel that serves the water heater is within sight, a second means of disconnect is not necessary. So a water heater that is in a garage or utility room with a direct sightline to the nearby panel serving it would be acceptable.
4) Pull disconnect or circuit breaker panel within sight - This is the solution we see most often in new construction.
2) Cord and plug within sight - Although we rarely see this option used anymore, you can wire the water heater with a cord to a wall receptacle that is within sight of the water heater. “Pulling the plug” is the most basic kind of disconnect there is.
3) Wall switch within sight - This is acceptable, but not necessarily the best choice, because eventually someone in the house will use the switch to try to turn on a light in the closet or room. After flipping it back and forth several times, they will decide that the switch doesn’t work, leaving it in the off position. Your next shower will be a cold one unless you label the switch as “WATER HEATER”. If you do choose this option, the switch be 30-amp rated (not a regular light switch).
5) Lockout device at panel - This is a metal gizmo that attaches permanently around the circuit breaker for the water heater in the electric panel, and is used when the panel is not within sight of the water heater. It has a hasp with a hole in it that accepts a small padlock, and allows the circuit breaker to literally be locked into the off position. Only a permanently installed lockout device is acceptable.
By the way, the first four options that are specified as “within sight” mean “within sight in both directions”: the switch should be visible from the appliance and the appliance visible from the switch. So, if the switch is just around a corner from where the water heater is located, and you can see it when standing at the switch, but the switch itself is not visible when you are at the water heater, it’s no good. The NEC also defines the range of “within sight” is maximum 50 feet away.
Prior to the 2017 edition of the National Electric Code, appliances rated at not over 300 volt amps (watts) or not over 1/8 hp motor were required to have a disconnect [NEC 422.31(a)], but it was not clear that it must be within sight if not lockable. The 2017 edition, however, added “where the switch or circuit breaker is within sight from the appliance” to the citation to clarify the intent.
• • • • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of more blog posts about WATER HEATERS:
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes