Can a doorbell transformer be installed inside an electric panel?
Saturday, June 30, 2018
The National Electrical Code (NEC 725.136A) specifically excludes any low voltage wiring from being installed in an electric panel, raceway, or box used for high voltage (120/240V) circuits. Electricians know better, but we regularly find homeowner-installed doorbell transformers sitting loose in the bottom of an electric panel, like in the photo above. This particular homeowner also attached flammable paper tags to the wiring to each breaker to identify the circuits—another no-no.
It is acceptable, however, to mount the doorbell transformer to the exterior of a surface mounted electric panel, and is usually done at the top of the panel.
• • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our other blog posts about ELECTRIC PANELS:
How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.