How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
When was GFCI-protection for kitchen dishwasher receptacle outlet first required?
Sunday, June 17, 2018
The requirement for GFCI-protection for the dishwasher receptacle was added with the 2014 edition of the National Electrical Code (NEC 210.8[C]). The only other kitchen location the NEC specifies GFCI-protection is the receptacles, where they are “installed to serve the countertop surfaces” [NEC210.8[A](8)]. So they are not required at regular wall receptacles in the kitchen.
While the year that the NEC added a new requirement is easy to define, each local juridiction’s building codes don’t necessarily adopt the latest edition of the NEC immediately. The state of Florida, for example, did not make the 2011 NEC effective until mid-2015. Other jurisdictions have sometimes waited even longer to adopt a newer NEC edition and, to complicate things further, they might make amendments that exclude parts of the newest requirements. So the year when the NEC first adds or changes a requirement can be several years before your local building department adopted that edition of the code and began enforcing it.
GFCI-receptacles have significantly reduced the number of electrocution since they began phasing in about 40 years ago, but there are several electrical hazards they do not protect against. See our blog posts Are Ground Fault Circuit Interrupters (GFCIs) really necessary and worth the trouble? and What electrical hazards does a Ground Fault Circuit Interrupter (GFCI) NOT protect against?
• • • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our other blog posts about AFCI and GFCI RECEPTACLES AND CIRCUIT BREAKERS:
• Does a septic pump or sump pump require a GFCI-receptacle?
• What is the difference between what trips a GFCI (ground fault) receptacle and a circuit breaker?
• What is the code requirement for GFCI protection for receptacles near a wet bar sink?
• When was GFCI-protection for kitchen dishwasher receptacle outlet first required?
• When did arc fault circuit interrupter (AFCI) breakers first become required?
• Does a washing machine receptacle outlet require GFCI protection?
• My spa tub stopped working. What's wrong?
• How do I identify a combination AFCI (CAFCI) circuit breaker?
• What does "listed and labeled" mean for an electrical component?
• What is the difference between GFCI and AFCI circuit breakers?
• Where are GFCI receptacle outlets required?
• When were GFCI receptacle outlets first required?
• What happens when you press the "TEST" button on a circuit breaker in an electric panel?
• What is the difference between the electric service to a mobile home and a site built home?
• Why is there a wall switch next to the furnace or indoor unit of the air conditioner in the garage?
• What is a Dual Function Circuit Interrupter (DFCI)?
• How I can tell if a receptacle outlet is tamper resistant?
• What is the difference between a Combination Arc Fault Circuit Interrupter (CAFCI) and an Arc Fault Circuit Interrupter (AFCI) circuit breaker?
• What is the difference between "grounded" and "grounding" electrical conductors?
• What does it mean when a wire is "overstripped" at a circuit breaker?
• Why is there a GFCI breaker in the electric panel for the bathroom shower light and exhaust fan?
• What is the switch on the wall with two pushbuttons?
• How far apart should kitchen counter receptacles be spaced?
• How far above a kitchen countertop do electrical outlets have to be?
• How is it possible to provide both GFCI (Ground Fault Circuit Interrupter) and CAFCI (Combination Arc Fault Circuit Interrupter) protection for kitchen and laundry circuits?
• My bathroom electric receptacle/outlet is dead and there are no tripped breakers in the electric panel. What's wrong?
• My GFCI reset button is hard to push and won't reset. What's wrong?
• Why do some breakers in my electric panel have a "TEST" button on them?
Visit our AFCI AND GFCI page for other related blog posts on this subject, or go to the INDEX for a complete listing of all our articles.
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.
Buying a home in North/Central Florida? Check our price for a team inspection by two FL-licensed contractors and inspectors. Over 8,500 inspections completed in 20+ years. In a hurry? We will get it done for you.