What is the required clearance for access and working space in front of a furnace or air handler?
Saturday, June 16, 2018
Although a furnace or air handler, like the heat pump one shown above, is part of a home HVAC system, it is an electric appliance. So the National Electrical Code requirement (NEC 110.26[A]) for equipment “likely to require examination, adjustment, servicing or maintenance while energized” applies, which specifies a working space 36” deep and 30” wide in front of the water heater.
The requirement for working space in front of a gas or oil-fired furnace would also be the same, because of the electric circuits in the appliance that are likely to require service.
• • • • • • • • • • • • • • • • • • • • • • • • •
To learn more about heating and air conditioning systems, see these other blog posts:
How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.