What are typical aluminum service entrance wire/cable sizes for the electrical service to a house?
Sunday, June 17, 2018
Here’s a listing of the standard aluminum service entrance wire sizes for residential 3-wire single-phase service. Wire sizes are AWG (American Wire Gauge), and variations may be possible due to temperature rating and type of wire.
SERVICE SIZE WIRE SIZE
100 amp #2
125 amp #1/0
150 amp #2/0
200 amp #4/0
225 amp #250
The neutral wire is often one or two sizes smaller than the two hots. The correct sizing of the neutral depends on doing a calculation of the “unbalanced load,” which is an estimate of the amount of 120-volt current usage.
Wire size may be marked on the side of the cable, followed by the letters “AWG,” like in the photo below. But not all cables are clearly marked and sometimes the lettering strip is just not visible. Electricians and experienced inspectors can tell at a glance if the service cable size is correct most of the time.
Aluminum wire sizes are usually one notch larger than copper for the same service rating. Also, the grey or black gooey stuff you will see around the aluminum wire lug connections is a required anti-oxidant paste.
The aluminum wire used for service cables and wiring for larger-amperage circuits in a home is multi-strand and a different metal composition that the solid aluminum wiring used during the early 1970s, that was later banned as a fire hazard.
• • • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our other blog posts about ELECTRICAL WIRING:
How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.