Is it alright to just put wire nuts on the end of unused or abandoned NM-cable or wiring?
Saturday, June 16, 2018
If the wiring is still connected at the other end in the electric panel, it must be terminated in an electrical box. The National Electrical Code (NEC 300.12) states that “Raceways, cable armors, and cable sheaths shall be continuous between cabinets, boxes, fittings, or other enclosures or outlets.” When the wiring is disconnected at both ends, then it should be removed. We see this situation most often under a kitchen sink where a disposal has been taken out, like in the photo above.
• • • • • • • • • • • • • • • • • • • • • • • • • • •
Here’s links to a collection of our other blog posts about AFCI and GFCI RECEPTACLES AND CIRCUIT BREAKERS:
How To Look At A House
McGarry and Madsen's home inspection blog for buyers of
site-built, mobile/manfuactured and modular homes
of Blog Posts
Top 5 results given instantly.
Click on magnifying glass
for all search results.